Monday, January 30, 2012
Specialist in Energy Policy
Richard J. Campbell
Specialist in Energy Policy
Mary Beth Nikitin
Specialist in Nonproliferation
The huge earthquake and tsunami that struck Japan’s Fukushima Daiichi nuclear power station on March 11, 2011, knocked out backup power systems that were needed to cool the reactors at the plant, causing three of them to undergo fuel melting, hydrogen explosions, and radioactive releases. Radioactive contamination from the Fukushima plant forced the evacuation of communities up to 25 miles away and affected up to 100,000 residents, although it did not cause any immediate deaths.
Tokyo Electric Power Company (TEPCO) operates the Fukushima nuclear power complex in the Futaba district of Fukushima prefecture in Northern Japan, consisting of six nuclear units at the Fukushima Daiichi station and four nuclear units at the Fukushima Daini station. All the units at the Fukushima complex are boiling water reactors, with reactors 1 to 5 at the Fukushima Daiichi site being the General Electric Mark I design, which is also used in the United States. The Fukushima Daiichi reactors entered commercial operation in the years from 1971 (reactor 1) to 1979 (reactor 6). The Fukushima Daini reactors shut down automatically after the earthquake and were able to maintain sufficient cooling.
When the earthquake struck, Fukushima Daiichi units 1, 2, and 3 were generating electricity and shut down automatically. The earthquake caused offsite power supplies to be lost, and backup diesel generators started up as designed to supply backup power. However, the subsequent tsunami flooded the electrical switchgear for the diesel generators, causing most AC power in units 1 to 4 to be lost. Because Unit 4 was undergoing a maintenance shutdown, all of its nuclear fuel had been removed and placed in the unit’s spent fuel storage pool. One generator continued operating to cool units 5 and 6.
The loss of all AC power in units 1 to 3 prevented valves and pumps from operating that were needed to remove heat and pressure that was being generated by the radioactive decay of the nuclear fuel in the reactor cores. As the fuel rods in the reactor cores overheated, they reacted with steam to produce large amounts of hydrogen, which escaped into the unit 1, 3, and 4 reactor buildings and exploded (the hydrogen that exploded in Unit 4 is believed to have come from Unit 3). The explosions interfered with efforts by plant workers to restore cooling and helped spread radioactivity. Cooling was also lost in the reactors’ spent fuel pools, although recent analysis has found that no significant overheating took place.
Radioactive material released into the atmosphere produced extremely high radiation dose rates near the plant and left large areas of land uninhabitable, especially to the northwest of the plant. Contaminated water from the plant was discharged into the sea, creating international controversy.
The United States and other countries, as well as the International Atomic Energy Agency, are providing assistance to Japan to deal with the nuclear disater. U.S. assistance has included transport of pumps, boron, fresh water, remote cameras, use of Global Hawk surveillance drones, evacuation support, medical support, and decontamination and radiation monitoring equipment.
Studies of the Fukushima disaster have identified design changes, response actions, and other safety improvements that could have reduced or eliminated the amount of radioactivity released from the plant. As a result, Fukushima has prompted a reexamination of nuclear plant safety requirements around the world, including in the United States.
Date of Report: January 18, 2012
Number of Pages: 15
Order Number: R41694
Follow us on TWITTER at http://www.twitter.com/alertsPHP or #CRSreports
Document available via e-mail as a pdf file or in paper form.
To order, e-mail Penny Hill Press or call us at 301-253-0881. Provide a Visa, MasterCard, American Express, or Discover card number, expiration date, and name on the card. Indicate whether you want e-mail or postal delivery. Phone orders are preferred and receive priority processing.
Posted by Penny Hill Press, Inc. at Monday, January 30, 2012